On May 3, 2016, the Centers for Medicare & Medicaid Services (CMS) announced a final rule (https://www.federalregister.gov/public-inspection) to update health care facilities’ fire protection guidelines to improve protections for all Medicare beneficiaries in facilities from fire.
The new guidelines apply to hospitals; long term care (LTC) facilities; critical access hospitals (CAHs); inpatient hospice facilities; programs for all inclusive care for the elderly (PACE); religious non-medical healthcare institutions (RNHCI); ambulatory surgical centers (ASCs); and intermediate care facilities for individuals with intellectual disabilities (ICF-IID).
This rule adopts updated provisions of the National Fire Protection Association’s (NFPA) 2012 edition of the Life Safety Code (LSC) as well as provisions of the NFPA’s 2012 edition of the Health Care Facilities Code. CMS strives to promote health and safety for all patients, family and staff in every provider and supplier setting. Fire safety requirements are an important part of this effort.
The provisions in this final rule cover construction, protection, and operational features designed to provide safety for Medicare beneficiaries from fire, smoke, and panic. Some of the main requirements laid out in this final rule include:
- Health care facilities located in buildings that are taller than 75 feet are required to install automatic sprinkler systems within 12 years after the rule’s effective date.
- Health care facilities are required to have a fire watch or building evacuation if their sprinkler systems is out of service for more than ten hours.
- The provisions offer LTC facilities greater flexibility in what they can place in corridors. Currently, they cannot include benches or other seating areas because of fire code requirements limiting potential barriers to firefighters. Moving forward, LTC facilities will be able to include more home-like items such as fixed seating in the corridor for resting and certain decorations in patient rooms (such as pictures and other items of home décor).
- Fireplaces will be permitted in smoke compartments without a one-hour fire wall rating, which makes a facility more home-like for residents.
- Cooking facilities now may have an opening to the hallway corridor. This will permit residents of inpatient facilities such as nursing homes to make food for themselves or others if they choose to, and, if the patient does decide to make food, facility staff is able to provide supervision of the patient.
- For ASCs, all doors to hazardous areas must be self-closing or must close automatically. Additionally, alcohol based hand rub dispensers now may be placed in corridors to allow for easier access.